The Association’s technical staff is available for consultation on specific issues relating to the specification or use of gypsum board. Most of the technical questions that arise are answered in one of the Gypsum Association publications; many specific gypsum and construction issues are addressed by one of the Association’s topical papers, and a large number of code and compliance matters are covered by one of the Evaluation Reports or code acceptances published by local, state, or model code bodies. Regardless of the published information available, there may be times when it is necessary to speak with or contact an expert on the subject.
Great numbers of questions regarding interpretations of Gypsum Association publications have been addressed by our technical experts. Issues and concerns that seem unique to a specific project often need the advice of someone specializing in gypsum board technology. However, what seems unique to a given project, may not be so unique. So, before you contact the technical department for help and advice, you might benefit from checking out the answers to Frequently Asked Questions (FAQs) below. FAQs are updated periodically, especially as seemingly unique questions recur.
Feel free to contact the Association staff by fax, phone, mail, or E-mail; we welcome the opportunity to assist you.
Q) Is it necessary to tape the joints in the base layers of fire-resistance rated multi-layer gypsum board systems to maintain the fire resistance rating?
A) No. In multi-layer systems, the joints and fasteners in the base layers are covered and protected by the overlying layers of gypsum board.
Q) The system I am installing calls for “cooler” nails. I am having trouble locating a supply of these nails in my area. What kind of nail can I substitute for the cooler nail?
A) Any nail having a length, shank diameter, and head diameter equal to or greater than the dimensions specified for the cooler nail in the system description can be substituted for the cooler nail.
Q) In a tested/listed fire assembly, what is the tolerance on the spacing of the fasteners described in the system?
A) Working with UL, the GA and its members have determined that approximately ± 1” (± 25.4 mm) is an acceptable tolerance in the spacing defined in a fire-rated assembly.
Q) Must gypsum wallboard be finished and painted?
A) According to ASTM C1396/C1396M Standard Specification for Gypsum Board, Section 13.1, “Gypsum board, except for pre-decorated gypsum board, is intended to be a substrate. The surfaces of gypsum board shall be true and free from imperfections that would render it unfit for finishing and final decoration. Gypsum board shall be installed and finished to the specified level in accordance with Specification C840.”
All gypsum wallboard used in interior wall and ceiling applications should be finished with tape and joint compound embedded in joints and interior angles, as well as an appropriate primer and paint. The application of these materials protects the integrity of gypsum wallboard. Note, in a fire-rated system that includes multiple layers of wallboard, only the final, visible, wallboard surface needs to be finished with tape, joint compound, primer and paint.
Exceptions can be made in areas that are concealed and received little or no active use, examples include attics and plenum areas above ceilings and attics. In these areas, tape and joint compound are required to provide fire resistance.
To determine the level of finish appropriate to a specific situation, including gypsum panel products used as a substrate for tile, as a base for textured finishes, wallcoverings, and paints of various sheens, and lighter and darker tones, consult GA-214-2015, Recommended Levels of Finish for Gypsum Board, Glass Mat and Fiber Reinforced Board, available in the GA Bookstore.
Q) What is a thermal barrier? What gypsum panel product(s) can be used as thermal barriers?
A) A thermal barrier is a material that provides some protection from heat for substances that can melt or burn. National Fire Protection Association (NFPA) standard NFPA 275 provides a method for qualifying the fire performance of a thermal barrier. The Temperature Transmission Fire Test and the Integrity Fire Test are used to evaluate a material’s capacity to prevent ignition from a standard fire exposure or to delay its occurrence. The code reference often reads as follows, “[Material in question] shall be separated from the interior of a building by an approved thermal barrier consisting of 1/2 -inch (12.7 mm) gypsum wallboard or a material that is tested in accordance with and meets the acceptance criteria of both the Temperature Transmission Fire Test and the Integrity Fire Test of NFPA 275.” As indicated in the text above, a ½” gypsum wallboard is a thermal barrier as would be wallboards of greater thickness when applied as part of a fire resistant system. Want to learn more? Read Thermal Barriers and Ignition Barriers for the Spray Polyurethane Foam Industry.
Q) What are the acceptable joint tolerances in gypsum construction?
A) Joints between boards in fire-rated assemblies must be in “moderate contact,” meaning that the boards should be touching and gaps minimal. All gaps and joints in such assemblies must be properly taped and filled with compund). Around electrical boxes, the UL Fire Resistance Directory references no more than a 1/8” (3.2 mm) gap/joint, though in the field this can be difficult to attain and measure. All gaps must be filled with joint compound, a fire-rated caulking or other materials/means suitable, per the local code authority. In non-rated construction, joints up to ¼” (6.4 mm) are acceptable when filled with setting type all-purpose joint compound. Note that the type of compound used to prefill gaps in the joints must be compatible with the compounds used to tape and finished the walls and/or ceiling.
More information on joint tolerance is contained in the Northwest Wall and Ceiling Bureau Document #500-103 Gaps at Gypsum Board Joints available here.
Q) The standard practice is to mount gypsum panel products such that a ¼” gap at exists between the board and the floor. Does this mean a fire-rated wall assembly needs to be caulked between the board and the floor?
A) More often than not, the answer is yes. In addition, fire-resistant walls often serve as a smoke barrier wall, which must be caulked. And, while some may see this as a control joint, the joint itself is not normally tested in most assemblies.The International Building Code addresses this firestopping in Section 715 as directed in Section 708:
708.8 Joints. Joints made in or between fire partitions shall comply with Section 715.
715.1 General. Joints installed in or between fire-resistance rated walls, floor or floor/ceiling assemblies and roofs or roof/ceiling assemblies shall be protected by an approved fire-resistant joint system designed to resist the passage of fire for a time period not less than the required fire-resistance rating of the wall, floor or roof in or between which the system is installed. Fire-resistant joint systems shall be tested in accordance with Section 715.3.
Exception: Fire-resistant joint systems shall not be required for joints in all of the following locations:
- Floors within a single dwelling unit.
- Floors where the joint is protected by a shaft enclosure in accordance with Section 713.
- Floors within atriums where the space adjacent to the atrium is included in the volume of the atrium for smoke control purposes.
- Floors within malls.
- Floors and ramps within open and enclosed parking garages or structures constructed in accordance with Sections 406.5 and 406.6, respectively.
- Mezzanine floors.
- Walls that are permitted to have unprotected openings.
- Roofs where openings are permitted.
- Control joints not exceeding a maximum width of 0.625 inch (15.9 mm) and tested in accordance with ASTM E 119 or UL 263.
715.1.1 Curtain wall assembly. The void created at the intersection of a floor/ceiling assembly and an exterior curtain wall assembly shall be protected in accordance with Section 715.4.
Additional information on the topic of firestopping can be obtained from a firestopping manufacturer or The International Firestop Council www.firestop.org/.
Q) What is an R-value and how can I calculate the R-value of a wall assembly shown in GA-600 Fire Resistance Design and Sound Control Manual? Finally, why am I being asked to do this?
A) R-value (resistance value) measures the capability of a material or assembly to resist the transmission of heat. As energy codes have strengthened over the past several code cycles, so have the R-value requirements for exterior walls and roof assemblies, in particular. As codes have become less prescriptive and more performance based, calculating R-values is becoming a part of every design teams’ duty.
The GA does not list R-values for wall assemblies due to the high degree of variability between what is shown in GA-600 and what is actually constructed. Common elements, such as resilient channels, thicker studs, decreased stud or joist spacing, varying amounts and types of insulation, etc., are variables that are allowed for any system, per the General Explanatory Notes in GA-600. Variables such as cladding type also play a role in total R-value.
However, calculating the R-value for an assembly is not exceptionally difficult, as it is essentially the sum of the R-value of the individual layers, accounting for stud closeness. ASHRAE, ICC, DOE and others have developed practices and methods for calculating R-value that are code acceptable. One online tool based on ASHRAE’s Handbook of Fundamentals information and practice is available at www.ekotrope.com/r-value-calculator/. A quick online search will provide additional online tools for performing these calculations.
Q) I understand that even Mold/Moisture Resistant Gypsum Panels should not be used in so-called “wet areas.” Can you explain where this product can and cannot be used?
A) Mold/Moisture Resistant Gypsum Panels are excellent for use in high humidity areas and even where an occasional splash of water is expected. Appropriate areas include powder rooms, adjacent to showers or tubs, behind counter areas/base cabinetry where plumbing fixtures are located, and in laundry rooms, mud rooms, etc.. However, neither the model codes nor the Tile Council of North America’s (TCNA) Handbook allow for the use of these boards behind the tile in the shower or tub area or as a base under the pan or around a swimming pool or sauna. For acceptable materials in wet areas, consult the local code or the TCNA.
Q) What guidance can the Gypsum Association provide on the painting and finishing of new gypsum wallboard?
Over the years, the Gypsum Association has worked with many organizations to develop recommendations on finishing. The most important recommendation is priming: Before any additional decoration, wallboard must be primed. For a more complete guide on painting and finishing new wallboard, we suggest the Drywall Finishing Council publication entitled, “Recommended Levels of Paint Finish Over Gypsum Board.” Access this publication here. Additionally, GA-214 Recommended Levels of Gypsum Board Finish, provides guidance for surface preparation. GA 214 is available in hardcopy or PDF in the Gypsum Association Bookstore.
Q) Is there guidance from the Gypsum Association on when drywall needs to be replaced after a fire?
The short answer is no. Any wallboard that has been damaged by fire or as a result of the firefighting process must be replaced; however, board that was simply exposed to smoke has no definitive replacement criteria. In this case, replacement will be determined on a case-by-case basis by the owner, contractor and insurance company.
The Gypsum Association publishes and revises numerous technical documents each year. Occasionally, the Association must issue an errata. The following errata is associated with section GA-216-2016, Application and Finishing of Gypsum Panel Products. On page 3, section 18.104.22.168 should read:
22.214.171.124 Where studs complying with ASTM C645 are used to receive Abuse Resistant or Impact Resistant Gypsum panels, they shall be not less than 0.0312 in. (0.792 mm) design thickness and shall be in accordance with sections 4.3 and 8.1 of Specification C645.
The correction clarifies the recommended thickness for steel studs receiving abuse resistant or impact resistant gypsum panels contained in GA-216-2016. The GA is communicating this errata as widely as possible. The electronic version of GA-216-2016 will reflect this change and hardcopies of Application and Finishing of Gypsum Panel Products are now issued with the clarification noted as an errata inserted on a separate sheet. Download a PDF copy of this errata for your records.